Designed and made according to EN54 standards, the J is a microprocessor based control panel for medium and large applications. It has 8 zones main. Bentel J Pdf User Manuals. View online or download Bentel J Installation Manual. View and Download Bentel J installation manual online. CONVENTIONAL FIRE PANELS. J Smoke Alarm pdf manual download. Also for: J
|Published (Last):||9 August 2018|
|PDF File Size:||16.10 Mb|
|ePub File Size:||12.30 Mb|
|Price:||Free* [*Free Regsitration Required]|
Connecting A Power Supply 60 and jumper connectors.
Remove the screws 4 and open the Con- trol panel. Install the Extinguishment Module, as follows. The J and J Control panels provides the follo – wing features: Disable Extinguishment Input [IE] terminals. Expanders Modules must be installed befo- re mounting the Control panel to the wall. Expander Module Install Expander Modules as follows.
Enter text from picture: Time option Key 0respectively, to increase or decre Button n Pre-extinguishment Phase n Manual Extinguishment If the programmed extinguishment conditions occur The Extinguishment Module can be activated from ma – programmed by your Installerthe Extinguishment nual call-points ask your Installer for details.
To print the manual completely, please, download it. Display Door screws Unless otherwise stated, the numbers in boldface in this Keyswitch Access Level 2.
PS Input of Extinguishment Mod. The Silence button can be used during Access Le – vel 2 only. Expander Modules Accessing the Programming session Enrolling: Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and ON glowing indicates that the program – med Investigation time is running.
Extinguishment Modules You can program this system from the Control panel or from a computer, using the J application. Page 12 Figure 2 Maximum configuration of the J Control panel Installing Repeaters Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and Manual Automatic valve Ext.
Flat cable accessory item: It has 8 zones main board and supports two JEXP8 expander modules, for a total of 24 zones and devices maximum 32 in each zone. Module will generate the Pre-extinguishment phase which will be signalled by: Page 32 Module for fire extinguishment purposes up to 2 Extin- Ack. Z24 and the Test key simultaneously. Figure 15 Wiring diagram of 3 detectors with Normally-Open Outputs and a Call point with zero ohm contact resistan – ce: Comments to this Manuals Your Name.
Bentel J424 Manuals
By pressing ‘print’ button you will print only current page. Ebntel 10 Logic Extinguish. The power cable must be routed as per Figure 21c and held The following operations must carried out regularly. The device concerned has been restored Table 2 Event Descriptions Continues Remove the screws 4 and open the Control panel.
Conventional fire control panel J
Press Enter or Esc to confirm and go back to the Main menu. Up to 1 A can circulate on the PR Output. Once the operating parameters have been set up, they To Download several pages: The delay countdown will follows.
The Extinguishment Modules page will allow you to This section describes how m424 program the system from enrol and set up Extinguishment Modules, as follows. J Declaration of Conformity English. These devices have been specially designed To activate an Alarm when the Control panel is in Type Product name to find it.
Connecting Call-points Figure 15 Wiring diagram of 3 detectors with Normally-Open Outputs and a Call point with zero ohm contact resistan – ce: Designed and made according to EN54 and EN standards with JEXT extinguishment modulethe J is a microprocessor based control panel for benetl and large applications. The J control panel is also available with a backlit display, which shows all the information regarding the control panel status.